Earth wire

In electrical engineering, ground or earth (symbol: ⏚) can refer to the reference point in an electrical circuit from which voltages are measured, a common return path for electric current, or a direct physical connection to the Earth.

Electrical circuits may be connected to ground (earth) for several reasons. In mains powered equipment, exposed metal parts are connected to ground to prevent user contact with dangerous voltage if electrical insulation fails. Connections to ground limit the build-up of static electricity when handling flammable products or electrostatic-sensitive devices.

In some telegraph and power transmission circuits, the earth itself can be used as one conductor of the circuit, saving the cost of installing a separate return conductor (see single-wire earth return).

For measurement purposes, the Earth serves as a (reasonably) constant potential reference against which other potentials can be measured. An electrical ground system should have an appropriate current-carrying capability to serve as an adequate zero-voltage reference level. In electronic circuit theory, a "ground" is usually idealized as an infinite source or sink for charge, which can absorb an unlimited amount of current without changing its potential. Where a real ground connection has a significant resistance, the approximation of zero potential is no longer valid. Stray voltages or earth potential rise effects will occur, which may create noise in signals or if large enough will produce an electric shock hazard.

The use of the term ground (or earth) is so common in electrical and electronics applications that circuits in portable electronic devices such as cell phones and media players as well as circuits in vehicles may be spoken of as having a "ground" connection without any actual connection to the Earth. This is usually a large conductor attached to one side of the power supply (such as the "ground plane" on a printed circuit board) which serves as the common return path for current from many different components in the circuit.

History
Long-distance electromagnetic telegraph systems from 1820 onwards used two or more wires to carry the signal and return currents. It was then discovered, probably by the German scientist Carl August Steinheil in 1836–1837, that the ground could be used as the return path to complete the circuit, making the return wire unnecessary. However, there were problems with this system, exemplified by the transcontinental telegraph line constructed in 1861 by the Western Union Company between Saint Joseph, Missouri, and Sacramento, California. During dry weather, the ground connection often developed a high resistance, requiring water to be poured on the ground rod to enable the telegraph to work or phones to ring.

Later, when telephony began to replace telegraphy, it was found that the currents in the earth induced by power systems, electrical railways, other telephone and telegraph circuits, and natural sources including lightning caused unacceptable interference to the audio signals, and the two-wire or 'metallic circuit' system was reintroduced around 1883.

Radio communications
An electrical connection to earth can be used as a reference potential for radio frequency signals for certain kinds of antennas. The part directly in contact with the earth - the "earth electrode" - can be as simple as a metal rod or stake driven into the earth, or a connection to buried metal water piping (the pipe must be conductive). Because high frequency signals can flow to earth due to capacitative effects, capacitance to ground is an important factor in effectiveness of signal grounds. Because of this, a complex system of buried rods and wires can be effective. An ideal signal ground maintains a fixed potential (zero) regardless of how much electric current flows into ground or out of ground. Low impedance at the signal frequency of the electrode-to-earth connection determines its quality, and that quality is improved by increasing the surface area of the electrode in contact with the earth, increasing the depth to which it is driven, using several connected ground rods, increasing the moisture content of the soil, improving the conductive mineral content of the soil, and increasing the land area covered by the ground system.

Some types of transmitting antenna systems in the VLF, LF, MF and lower SW range must have a good ground to operate efficiently. For example, a vertical monopole antenna requires a ground plane that often consists of an interconnected network of wires running radially away from the base of the antenna for a distance about equal to the height of the antenna. Sometimes a counterpoise is used as a ground plane, supported above the ground.

AC power wiring installations
In a mains electricity (AC power) wiring installation, the term ground conductor typically refers to three different conductors or conductor systems as listed below.

Equipment earthing conductors provide an electrical connection between non-current-carrying metallic parts of equipment and the earth. According to the U.S. National Electrical Code (NEC), the reason for doing this is to limit the voltage imposed by lightning, line surges, and contact with higher voltage lines. The equipment earthing conductor is usually also used as the equipment bonding conductor (see below).

Equipment bonding conductors provide a low impedance path between non-current-carrying metallic parts of equipment and one of the conductors of that electrical system's source, so that if a part becomes energized for any reason, such as a frayed or damaged conductor, a short circuit will occur and operate a circuit breaker or fuse to disconnect the faulted circuit. Note that the earth itself has no role in this fault-clearing process since current must return to its source, not the earth as is sometimes believed (see Kirchhoff's circuit laws). By bonding (interconnecting) all exposed non-current carrying metal objects together, they should remain near the same potential thus reducing the chance of a shock. This is especially important in bathrooms where one may be in contact with several different metallic systems such as supply and drain pipes and appliance frames. The equipment bonding conductor is usually also used as the equipment earthing conductor (see above).

A grounding electrode conductor connects one leg of an electrical system to one or more earth electrodes. This is called "system grounding" and most systems are required to be grounded. The U.S. NEC and the UK's BS 7671 list systems that are required to be grounded. The grounding electrode conductor is connected to the leg of the electrical system that is the "neutral wire". The grounding electrode conductor is also usually bonded to pipework and structural steel in larger structures. According to the NEC, the purpose of earthing an electrical system is to limit the voltage to earth imposed by lightning events and contact with higher voltage lines, and also to stabilize the voltage to earth during normal operation. In the past, water supply pipes were often used as ground electrodes, but this was banned where plastic pipes are popular. This type of ground applies to radio antennas and to lightning protection systems.

Permanently installed electrical equipment usually also has permanently connected grounding conductors. Portable electrical devices with metal cases may have them connected to earth ground by a pin in the interconnecting plug (see Domestic AC power plugs and sockets). The size of power ground conductors is usually regulated by local or national wiring regulations.

Power transmission
In Single Wire Earth Return (SWER) AC electrical distribution systems, costs are saved by using just a single high voltage conductor for the power grid, while routing the AC return current through the earth. This system is mostly used in rural areas where large earth currents will not otherwise cause hazards.

Some high-voltage direct-current (HVDC) power transmission systems use the ground as second conductor. This is especially common in schemes with submarine cables, as sea water is a good conductor. Buried grounding electrodes are used to make the connection to the earth. The site of these electrodes must be chosen carefully to prevent electrochemical corrosion on underground structures.

A particular concern in design of electrical substations is earth potential rise. When very large fault currents are injected into the earth, the area around the point of injection may rise to a high potential with respect to distant points. This is due to the limited finite conductivity of the layers of soil in the earth. The gradient of the voltage (changing voltage within a distance) may be so high that two points on the ground may be at significantly different potentials, creating a hazard to anyone standing on the ground in the area. Pipes, rails, or communication wires entering a substation may see different ground potentials inside and outside the substation, creating a dangerous touch voltage.

Electronics

 * - align = "center"
 * [[Image:Signal Ground.svg]]
 * width = "25"|
 * [[Image:Chassis Ground.svg]]
 * width = "25"|
 * [[Image:Earth Ground.svg]]
 * - align = "center"
 * Signal ground
 * Chassis ground
 * Earth ground
 * Earth ground
 * Earth ground

Signal grounds serve as return paths for signals and power (at extra low voltages, less than about 50 V) within equipment, and on the signal interconnections between equipment. Many electronic designs feature a single return that acts as a reference for all signals. Power and signal grounds often get connected, usually through the metal case of the equipment.

Circuit ground versus earth
Voltage is a differential quantity. To measure the voltage of a single point, a reference point must be selected to measure against. This common reference point is called "ground" and considered to have zero voltage. This signal ground may not be connected to a power ground. A system where the system ground is not connected to another circuit or to earth (though there may still be AC coupling) is often referred to as a floating ground.

Separating low signal ground from a noisy ground
In television stations, recording studios, and other installations where sound quality is critical, a special signal ground known as a "technical ground" (or "technical earth", "special earth" and "audio earth") is often installed, to prevent ground loops. This is basically the same thing as an AC power ground, but no general appliance ground wires are allowed any connection to it, as they may carry electrical interference. For example only audio equipment is connected to the technical ground in a recording studio. In most cases, the studio's metal equipment racks are all joined together with heavy copper cables (or flattened copper tubing or busbars) and similar connections are made to the technical ground. Great care is taken that no general chassis grounded appliances are placed on the racks, as a single AC ground connection to the technical ground will destroy its effectiveness. For particularly demanding applications, the main technical ground may consist of a heavy copper pipe, if necessary fitted by drilling through several concrete floors, such that all technical grounds may be connected by the shortest possible path to a grounding rod in the basement.

Lightning protection systems
Lightning protection systems are designed to mitigate the effects of lightning through connection to extensive grounding systems that provide a large surface area connection to earth. The large area is required to dissipate the high current of a lightning strike without damaging the system conductors by excess heat. Since lightning strikes are pulses of energy with very high frequency components, grounding systems for lighting protection tend to use short straight runs of conductors to reduce the self-inductance and skin effect.

Earthing system
In electricity supply systems, an earthing (grounding) system defines the electrical potential of the conductors relative to that of the Earth's conductive surface. The choice of earthing system has implications for the safety and electromagnetic compatibility of the power supply. Note that regulations for earthing systems vary considerably between different countries.

A functional earth connection serves a purpose other than providing protection against electrical shock. In contrast to a protective earth connection, a functional earth connection may carry a current during the normal operation of a device. Functional earth connections may be required by devices such as surge suppression and electromagnetic-compatibility filters, some types of antennas and various measurement instruments. Generally the protective earth is also used as a functional earth, though this requires care in some situations.

Bonding
Strictly speaking, the terms grounding or earthing are meant to refer to an electrical connection to ground/earth. Bonding is the practice of intentionally electrically connecting metallic items not designed to carry electricity. This brings all the bonded items to the same electrical potential as a protection from electrical shock. The bonded items can then be connected to ground to bring them to earth potential.

Ground (earth) mat
A ground (earth) mat or grounding (earthing) mat is a flat, flexible pad used for working on electrostatic sensitive devices. It is generally made of a conductive plastic or metal mesh covered substrate which is electrically attached to ground (earth). This helps discharge any static charge which a worker has built up, as well as any static charge on tools or exposed components laid on the mat. It is used most commonly in computer repair. Ground (earth) mats are also found on fuel trucks and tankers, which are otherwise insulated from ground (earth) as they make physical contact only with their tires and the air; obviously static discharge is undesirable during fuel-transfer operations. Similarly, in aircraft refueling, a ground (earth) cable connects the tanker (truck or airplane) to the fuel-seeking craft to eliminate charge differences before fuel is transferred.

In an electrical substation a ground (earth) mat is a mesh of conductive material installed at places where a person would stand to operate a switch or other apparatus; it is bonded to the local supporting metal structure and to the handle of the switchgear, so that the operator will not be exposed to a high differential voltage due to a fault in the substation.

Isolation
Isolation is a mechanism that defeats grounding. It is frequently used with low-power consumer devices, and when electronics engineers, hobbyists, or repairmen are working on circuits that would normally be operated using the power line voltage. Isolation can be accomplished by simply placing a "1:1 wire ratio" transformer with an equal number of turns between the device and the regular power service, but applies to any type of transformer using two or more coils electrically insulated from each other.

For an isolated device, touching a single powered conductor does not cause a severe shock, because there is no path back to the other conductor through the ground. However, shocks and electrocution may still occur if both poles of the transformer are contacted by bare skin. Previously it was suggested that repairmen "work with one hand behind their back" to avoid touching two parts of the device under test at the same time, thereby preventing a circuit from crossing through the chest and interrupting cardiac rhythms/ causing cardiac arrest.

Generally every AC power line transformer acts as an isolation transformer, and every step up or down has the potential to form an isolated circuit. However, this isolation would prevent failed devices from blowing fuses when shorted to their ground conductor. The isolation that could be created by each transformer is defeated by always having one leg of the transformers grounded, on both sides of the input and output transformer coils. Power lines also typically ground one specific wire at every pole, to ensure current equalization from pole to pole if a short to ground is occurring.

In the past, grounded appliances have been designed with internal isolation to a degree that allowed the simple disconnection of ground by cheater plugs without apparent problem (a dangerous practice, since the safety of the resulting floating equipment relies on the insulation in its power transformer). Modern appliances however often include power entry modules which are designed with deliberate capacitive coupling between the AC power lines and chassis, to suppress electromagnetic interference. This results in a significant leakage current from the power lines to ground. If the ground is disconnected by a cheater plug or by accident, the resulting leakage current can cause mild shocks, even without any fault in the equipment. Even small leakage currents are a significant concern in medical settings, as the accidental disconnection of ground can introduce these currents into sensitive parts of the human body. As a result, medical power supplies are designed to have low capacitance.

Class II appliances and power supplies (such as cell phone chargers) do not provide any ground connection, and are designed to isolate the output from input. Safety is ensured by double-insulation, so that two failures of insulation are required to cause a shock.

Types of Industrial Grounding Systems
Types of industrial grounding systems include:


 * Solidly grounded systems.
 * Low-resistance grounding systems.
 * High-resistance grounding (HRG) systems.

Low-resistance grounding systems use a neutral grounding resistor (NGR) to limit the fault current to 25 A or greater. Low resistance grounding systems will have a time rating (e.g. 10 seconds) that indicates how long the resistor can carry the fault current before overheating. A ground fault protection relay must trip the breaker to protect the circuit before overheating occurs. High-resistance grounding (HRG) systems use an NGR to limit the fault current to 25 A or less. They have a continuous rating, and are designed to operate with a single-ground fault. This means that the system will not immediately trip on the first ground fault. If a second ground fault occurs, a ground fault protection relay must trip the breaker to protect the circuit. On an HRG system, a sensing resistor is used to continuously monitor system continuity. If an open-circuit is detected (e.g., due to a broken weld on the NGR), the monitoring device will sense voltage through the sensing resistor and trip the breaker. Without a sensing resistor, the system could continue to operate without ground protection (since an open circuit condition would mask the ground fault) and transient overvoltages could occur.